|Place of Origin:||China|
Payment & Shipping Terms:
|Minimum Order Quantity:||1set system|
|Packaging Details:||Plywood case or box case|
|Delivery Time:||10-15 working days|
|Payment Terms:||L/C, D/P, T/T, Western Union, Paypal, Credit card|
|Supply Ability:||300 sets per month|
|Standard Of Examination:||GB25972-2010||Capacity Of Cylinder:||180L|
|Max Working Pressure:||5.3Mpa||Storage Pressure:||4.2Mpa|
Clean Gas Fm 200 Extinguishing System Preparation For Storage Room
1.Clean gas, colorless and tasteless and non-corrosive
2. No damage to ozone layer
3. Totally automatic system
4. Manual or electromagnetic manipulation and mechanical manipulation
5. Short time discharge of extinguishing agent
6. Preparation for storage room
Electronic computer room, a data processing center, telecommunications facilities, process control, expensive medical equipment, industrial equipment, library, museum and art gallery, clean room, chamber, emergency power facilities, flammable liquid storage area, etc.
The place where the fire is easy to happen, like paint-spraying production line, aging-electrical equipment, rolling machine, printing machine, oil switch, oil immersed transformer, melt impregnating tank, tank, large generators, drying equipment, cement production process of pulverized coal, and the ship's engine room, cargo hold, etc.
|2||Scale of Protective region for one zone||area:max single-zone is 800m2 volume:max single-zone is 3600m3|
|6||Nitrogen Pressure of Driving Device||6.0±1.0Mpa(20℃)|
|7||Condition of reserving room for container||temperature: -10~50℃, relative humidity: ≤97%|
|8||max working pressure||5.3Mpa|
|9||min working pressure||4.2Mpa
Pipe network fm200 fire suppression device is composed of the follow-up components: fm200 agent, fm200 cylinders, container valves, flexible hoses, liquid flow check valves, a set of manifold, a safety valve, pressure switch, nitrogen driving device(s), driving device frame, gas control pipe, gas flow check valves(it depends), selective valves(it depends), a pair of elbows and flanges, nozzles.If one set device needs to protect multiple protected zones, its composition is as above. However, if one set system just needs to protected single protected zone, the gas flow check valve and the selective valve should be got rid of from its composition.
the method of putting out fire: whole flooding
the sample working way: fire happens → the smoke and heat detector send signal back to the control panel
→ the control panel gets the signal and activates alarm bell → after a few seconds
delay, the fire extinguishing device activates and put out the fire.