Payment & Shipping Terms:
|Type:||Piped Network||Function:||Fire Suppression|
|Filling Pressure:||5.6Mpa||Pattern Of Extinguishing:||Enclosed Flooding|
|Nitrogen Pressure Of Driving Device:||6.0±1.0Mpa(20℃)||Actuation:||Automatic Or Manual|
5.6Mpa Residential Hfc-227Ea Extinguishing System 180L Storage
|2||Scale of Protective region for one zone||area:max single-zone is 800m² volume:max single-zone is 3600m³|
|6||Nitrogen Pressure of Driving Device||6.0±1.0Mpa(20℃)|
|7||Condition of reserving room for container||temperature: -10~50℃, relative humidity: ≤97%|
|8||max working pressure||8.0Mpa|
|9||min working pressure||4.6Mpa|
1. Clean gas, colorless and tasteless and non-corrosive
2. Electric insulation, utilization for extinguishing of electrical combustion
3. No residue and pollution inside protection zone
4. No damage to ozone layer
5. Totally automatic system
6. Accurate control of protection zone
7. No need for employment of monitor staff
8. Manual or electromagnetic manipulation and mechanical manipulation
FM200 fire suppression is suitable for occupied room, because of its working principle is whole flooding. Those places that easily get fire require our fire suppression system. Taking the followings as examples:
Data and paper archives
Switch gear rooms
Military applications and cell sites
Records and data archives
Electric utility facilities
Hfc227ea Fire Suppression System With 180l Storage In 5.6mpa is mainly composed by three parts. Extinguishing devices and pipe fittings and electrical accessories.
Extinguishing devices are such things, like cylinder to fill and store fm200, frame and driving device(nitrogen cylinder) to trigger the storage cylinder to discharge agent and so on.
Pipe fittings are those conduits to connect extinguishing device and guide agent into protective zone, like high pressure galvanized steel pipe and flange and elbow and so on.
Electrical accessories are those things which are used to detect and monitor whole protective area and control whole system, also warn people to evacuate and prevent from fire expansion.
These integrated three parts will be efficient to detect and supervise and alarm and extinguish fire automatically.
Here attached below is complete composition of whole system,
Here is the illustration of working principle to whole system,