|Place of Origin:||China|
Payment & Shipping Terms:
|Minimum Order Quantity:||1 set of system|
|Packaging Details:||Plywood case or box case|
|Delivery Time:||10-15 working days|
|Payment Terms:||L/C, D/P, T/T, Western Union, Paypal, Credit card|
|Supply Ability:||3000 sets per month|
|Nitrogen Pressure Of Driving Device:||6.0±1.0Mpa(20℃)||Spraying Time:||≤60s|
|Pattern Of Extinguishing:||Enclosed Flooding||Working Pressure:||5.7MPa|
|Cylinder Volume:||70L||Capacity Of Agent:||42kg|
|Type:||Pipe Network||Starting Mode:||Automatic, Electrical Manual, Mechanical Emergency Manual|
5.7MPa Automatic Fire Extinguishing System,
0.6kg/L Automatic Fire Extinguishing System
CO2 automatic fire extinguishing system
Fire suppression systems are designed to suppress or extinguish a fire in sensitive environments where water from a fire sprinkler is not a desired extinguishing agent. Common areas where you will find fire suppression systems include server rooms, engine rooms, flammable storage areas, museums, and data centers.
There are a few different types of agents that are used in a suppression system to suppress the fire. In server rooms and environments where you have personnel working in the area, you will usually find clean agent or inert gas suppression systems. In environments where there are few personnel or none at all, you will typically find CO2 fire suppression systems. The areas that you’ll find CO2 fire suppression systems include engine rooms, generator rooms, power stations, flammable liquid storage rooms, and around large industrial machines.
While CO2 fire suppression systems are highly effective at suppressing fires, the CO2 agent also poses a health risk when compared to the other agents. For this reason, you’ll find CO2 fire suppression systems most often in non-occupied environments.
|3||Filling Volume of Gas||42kg|
|5||Max Working Pressure||12.4MPa|
|7||Max Filling Rate||0.6kg/L|
|9||Working Pressure of Releasing Device||Container Valve: 19±0.95MPa;
|10||Nitrogen Pressure of Driving||6.0±1.0Mpa(20℃)|
|11||Condition of Reserving Room for Container||Temperature: 0~50℃|
Pipe network type of CO2 automatic fire suppression system is mainly composed by three parts. Extinguishing devices and pipe fittings and electrical accessories.
Extinguishing devices are such things, like cylinder to fill and store CO2, frame and driving device(nitrogen cylinder) to trigger the storage cylinder to discharge agent and so on.
Pipe fittings are those conduits to connect extinguishing device and guide agent into protective zone, like high pressure galvanized steel pipe and flange and elbow and so on.
Electrical accessories are those things which are used to detect and monitor whole protective area and control whole system, also warn people to evacuate and prevent from fire expansion.
These integrated three parts will be efficient to detect and supervise and alarm and extinguish fire automatically.
Enter Your Message