|Place of Origin:||China|
Payment & Shipping Terms:
|Minimum Order Quantity:||5 sets|
|Packaging Details:||Plywood case|
|Delivery Time:||10-15 working days after payment or receipt of L/C|
|Payment Terms:||L/C, , D/P, T/T, Western Union, Paypal, Credit card|
|Supply Ability:||200 sets per week|
|Discharge Type:||Indirect||Capacity Of Agent:||42kg|
|Agent:||Carbon Dioxide||Material:||Steel Cylinder|
|Standard Of Examination:||GB25972-2010||Volume:||70L|
fire detection tubing,
fire extinguisher tube
Hfc 227ea Fire Detection Tube For Communications , Broadcasting
|1||Type||Carbon dioxide direct type|
|4||Max working pressure||12.1Mpa|
|6||Density of unit volume||2.5kg/m3|
|7||Max length of detecting tube||25m|
|8||Quantity of agent||42kg|
The fm200 fire trace extinguisher is a kind of clean, colorless and odorless fire suppression system. Because of its pure and environmentally friendly characteristic, it is widely recognized as the proper substitute to the halon series. This kind of system depends neither electric starting nor manual starting, so even if there is power cut, the fire suppression system can stay in working condition.
The fm200 fire trace extinguisher should be fixed to the outer cabinet, and fasten the fire detecting tube above or near the places that a fire easily happens. This action will help the system activate in time when a fire occurs, because the system activates only when the detecting tube is burnt by the fire.
As its appearance shows, the fm200 fire trace suppression system is used to protect machinery equipment like the power plants, communications, broadcasting, petrochemical, railway ans so on system.
The direct type fire detecting tube fire suppression system is consist of a cylinder, an at most 25m long fire detecting tube, a container valve and two kinds of agents-- co2 and fm200.
The indirect type fire detecting tube fire suppression system has the same components as the direct type except a release tube added. In this system, the fire detecting tube is used for just detecting function, so it needs a release tube together, however, for the direct type, the fire detecting tube can be used for both detecting and releasing.
1 / After finishing putting out fire, the fm200 fire trace suppression system should have a whole check and refill.
2 / A complete routine check of the fm200 fire trace suppression system should be done at least once a year. If can follow the frequency we suggest in the manual instruction that will be better.
3 / Any problem occurs, we suggest that users should neither touch nor even want to fix it by themselves, but phone us at the first time to tell us that there is a problem and we will send our professionals to fix it as soon as possible.
4 / We suggest that after everything in the protected zone is ready, then can users begin installing the fm200 fire trace suppression system in case of mistaken opening the fire suppression system.