|Place of Origin:||China|
Payment & Shipping Terms:
|Minimum Order Quantity:||30 set|
|Packaging Details:||Plywood case,Paper carton|
|Delivery Time:||10-15 working days after payment or receipt of L/C|
|Payment Terms:||L/C, T/T, D/P, Western Union，Paypal,Credit Crad,Debit Card|
|Supply Ability:||1000 set per month|
|Storage Pressure:||1.6Mpa||Capacity Of Cylinder:||8L|
|Zone Management:||Single||Pattern Of Extinguishing:||Enclosed Flooding|
8L Automatic Fire Extinguisher,
1.6Mpa Automatic Fire Extinguisher
1.6Mpa 8L Carbon Dioxide Automatic Fire Extinguisher in Suspension
8L Automatic Fire Extinguisher In Suspension started by temperature, when surrounding temperature reaches the setting value, the temperature sensing glass ball will be burnt, releasing extinguishing agents to put out the fire.
Electronic computer room, a data processing center, telecommunications facilities, process control, expensive medical equipment, industrial equipment, library, museum and art gallery, etc.
The place where the fire is easy to happen, like paint-spraying production line, aging-electrical equipment, rolling machine, printing machine, oil switch, oil immersed transformer, melt impregnating tank, tank, large generators, drying equipment, cement production process of pulverized coal, and the ship's engine room, cargo hold, etc.
Below attached is one mimic diagram of 8l Automatic Fire Extinguisher In Suspension type.
1 / We suggest that there should be at least a yearly routine check for the whole system. Actually, some components need check weekly, some monthly and the whole system yearly. The frequency of checking better follows the manual instruction we provide.
2 / If there is any problem, users should not touch anything even try to fix it themselves, because an unprofessional repair can make things worse. The best plan we suggested when the system has something wrong is that users should wait for our professionals there to repair and fix it.
3 / In our professional considerations, we suggest that one protected room better should not install more than one temperature-based fm200 fire extinguisher. When there is a fire, the temperature of some space near the fire point will go up and some far away point stay cool. Thus this temperature difference is unable to let the fire extinguisher start at the same time, which makes the fire agent cannot ran out within 8s and fails to protect the possession in the room.
The electromagnetic hanging type fm200 fire suppression system:
A fire happens → A smoke / heat detector activates and send a signal to the control panel → control panel receives the signal and activate the alarm bell to notify people that quickly escape from the building → control panel receive both signals from smoke and heat detector, and then activate the electromagnetic hanging type fm200 fire suppression system.
The temperature-based hanging type fm200 fire extinguisher:
A fire happens → the temperature climbs high fast → temperature exceeds the specified temperature of the temperature sensing glass ball → the temperature sensing glass ball is burnt by the high temperature → the fm200 fire agent comes out from the cylinder through nozzle for putting out the fire.