|Place of Origin:||China|
Payment & Shipping Terms:
|Minimum Order Quantity:||1set system|
|Packaging Details:||Plywood case or box case|
|Delivery Time:||10-15 working days|
|Payment Terms:||L/C, D/P, T/T, Western Union, Paypal, Credit card|
|Supply Ability:||300 sets per month|
|Storage Pressure:||4.2Mpa||Capacity Of Cylinder:||70L|
|Actuation:||Automatic Or Manual||Agent:||Fm200|
fm 200 suppression system,
fire safety solutions
Industrial 70L Model FM200 Gas Suppression System Hfc 227 Gas
|2||Scale of Protective region for one zone||area:max single-zone is 800m2 volume:max single-zone is 3600m3|
|6||Nitrogen Pressure of Driving Device||6.0±1.0Mpa(20℃)|
|7||Condition of reserving room for container||temperature: -10~50℃, relative humidity: ≤97%|
|8||max working pressure||5.3Mpa|
|9||min working pressure||4.2Mpa|
In terms of description of agent, one of its competent advantages is that it can be used for all kinds of class fires except metal fire. And it is clean agent. There is no residue and pollution after extinguishing.
Another one is that fm200 extinguishing system is special for critical assets or device. It will have no damage for your property. Relatively, it is cheap and effective to be chosen as fire suppression system.
It is very efficient for you to protect your possession. Since it is a system, it include extinguishing device to put out fire at short time, specially, shorter than 10 second. It means all agent will be discharged in so short time. Then it will be flooding overall. In addition, it has time-delay mechanism. It is around 2 minute. It means when fire happens, there is enough time left to evacuate people from hazardous place.
It can let multiple zones are protectively in the control of one system. Then it will save much money for big and multiple zones.
Here is the illustration of working principle to whole system,
Pipe network fm200 fire suppression device is composed of the following components: fm200 agent, fm200 cylinders, container valves, flexible hoses, liquid flow check valves, a set of manifold, a safety valve, pressure switch, nitrogen driving device(s), driving device frame, gas control pipe, gas flow check valves(it depends), selective valves(it depends), a pair of elbows and flanges, nozzles.
If one set device needs to protect multiple protected zones, its composition is as above. However, if one set system just needs to protected single protected zone, the gas flow check valve and selective valve should be got rid of from its composition.
Below attached is one mimic diagram of 4.2Mpa 70L Model Fm200 Firefighting System