Payment & Shipping Terms:
|Dimension(mm):||450*400*1450||Capacity Of Cylinder:||40L|
|Standard Of Examination:||GB25972-2010||Pattern Of Extinguishing:||Enclosed Flooding|
|Volume Of Cabinet:||261L||Weight:||33kg|
Commercial 40L FM200 Fire Extinguishing System For Single Zone
1. Agent quantity for biggest zone is enough to protect all zones through selector valves
2. Direct target to expensive machine or delicate device
3. Short time discharge of extinguishing agent
4. Preparation for storage room
5. Space confirmation of placement for cylinder group
|6||max working pressure||4.2Mpa|
The place where the fire is easy to happen, like paint-spraying production line, aging-electrical equipment, rolling machine, printing machine, oil switch, oil immersed transformer, melt impregnating tank, tank, large generators, drying equipment, cement production process of pulverized coal, and the ship's engine room, cargo hold, etc.
40l Hfc227ea Firefighting System For Single Zone is mainly composed by two parts. Extinguishing devices and electrical accessories.
Extinguishing devices are such things, like cabinet to store extinguishing device, cylinder to fill and store fm200 and flexible hose and solenoid actuator and so on.
Electrical accessories are those things which are used to detect and monitor whole protective area and control whole system, also warn people to evacuate and prevent from fire expansion.
These integrated two parts will be efficient to detect and supervise and alarm and extinguish fire automatically.
Here attached below is complete composition of whole system,
Cabinet fm200 fire suppression system has a large number of advantages, and here is going to have a brief explanation:
1/ Swift response. Since there is no long distance transportation of pipes, so fm200 gas can be directly discharged into protection zone. Meanwhile, its spraying time is less than 8 second. So it will save more time relatively when the fire happens.
2/ Convenient installation. Compared with pipe network system, cabinet system would be relatively simple to conduct installation. After installation of control panels and electric components, left work is just to connect it with one cabinet fire extinguishing device or devices. But one room should not be matched with more than 4 pieces of it because of the limitation of the output current of a control panel.
3/ Lower cost. Obviously, the price would be cheaper than pipe network type for the protection zone which just needs one single cylinder, because there is no need to consider about the expense of pipes and pipe fittings, also the cost of manpower for this part.
Contact Person: xingjin