Payment & Shipping Terms:
|Storage Pressure:||5.6Mpa||Zone Management:||One Zone|
|Max Working Pressure:||8.0Mpa||Min Working Pressure:||4.6Mpa|
|Pattern Of Extinguishing:||Enclosed Flooding||Standard Of Examination:||GB25972-2010|
Single Zone 5.6Mpa Hfc227Ea Fire Suppression Systems For Cargo Hold
1. Totally automatic system
2. Accurate control of protection zone
3. No need for employment of monitor staff
4. Manual or electromagnetic manipulation and mechanical manipulation
5. Multiple management in the control of the whole system
6. Agent quantity for biggest zone is enough to protect all zones through selector valves
7. Direct target to expensive machine or delicate device
|2||Scale of Protective region for one zone||area:max single-zone is 800m² volume:max single-zone is 3600m³|
|6||Nitrogen Pressure of Driving Device||6.0±1.0Mpa(20℃)|
|7||Condition of reserving room for container||temperature: -10~50℃, relative humidity: ≤97%|
|8||max working pressure||8.0Mpa|
|9||min working pressure||4.6Mpa|
The place where the fire is easy to happen, like paint-spraying production line, aging-electrical equipment, rolling machine, printing machine, oil switch, oil immersed transformer, melt impregnating tank, tank, large generators, drying equipment, cement pro duction process of pulverized coal, and the ship's engine room, cargo hold, etc.
In terms of description of agent, one of its competent advantages is that it can be used for all kinds of class fires except metal fire. And it is clean agent. There is no residue and pollution after extinguishing.
Another one is that fm200 extinguishing system is special for critical assets or device. It will have no damage for your property. Relatively, it is cheap and effective to be chosen as fire suppression system.
It is very efficient for you to protect your possession. Since it is a system, it include extinguishing device to put out fire at short time, specially, shorter than 10 second. It means all agent will be discharged in so short time. Then it will be flooding overall. In addition, it has time-delay mechanism. It is around 2 minute. It means when fire happens, there is enough time left to evacuate people from hazardous place.