|Place of Origin:||China|
Payment & Shipping Terms:
|Minimum Order Quantity:||1set system|
|Packaging Details:||Plywood case,Paper carton|
|Delivery Time:||10-15 working days after payment or receipt of L/C|
|Payment Terms:||L/C, T/T, D/P, Western Union,Paypal,Credit Card,Debit Card|
|Supply Ability:||3,00 set per month|
|With Pipe Network Or Not:||No Pipe Network||Type:||Cabinet|
|Capacity Of Cylinder:||40L||Actuation:||Automatic Or Manual|
Non-corrosive HFC227ea Fire Suppression System of Cabinet 40L Type
|6||Max working pressure||4.2Mpa|
1. Clean gas, colorless and tasteless and non-corrosive
2. Totally automatic system
3. Accurate control of protection zone
4. Short time discharge of extinguishing agent
5. Preparation for storage room
6. Space confirmation of placement for cylinder group
Electronic computer room, a data processing center, telecommunications facilities, process control, expensive medical equipment, industrial equipment, library, museum and art gallery, clean room, anechoic chamber, emergency power facilities, flammable liquid storage area, etc.
The place where the fire is easy to happen, like paint-spraying production line, aging-electrical equipment, rolling machine, printing machine, oil switch, oil immersed transformer, melt impregnating tank, tank, large generators, drying equipment, cement pro duction process of pulverized coal, and the ship's engine room, cargo hold, etc.
FM200 Gas Suppression System of cabinet 40L type is mainly composed by two parts. Extinguishing devices and electrical accessories.
Extinguishing devices are such things, like cabinet to store extinguishing device, cylinder to fill and store fm200 and flexible hose ans solenoid actuator and so on.
Electrical accessories are those things which are used to detect and monitor whole protective area and control whole system, also warn people to evacuate and prevent from fire expansion.
These integrated two parts will be efficient to detect and supervise and alarm and extinguish fire automatically.
Here attached below is complete composition of whole system,
There are some points users need to notice when they are using this system.
1/ The volume of the protected zone shouldn't be bigger than 1600 cubic metres; the proportion of the protected zone should be smaller than 500 square metres.
2/ If there some problems occur, users shouldn't fix or touch it themselves. The best solution is to call and tell us the problems, and wait for our professionals.
3/ Users better follow the routine check schedual that we provide.
4/ unless everthing is at its position, the cover of the small ball valve can be unclosed.