Payment & Shipping Terms:
|Filling Pressure:||1.6Mpa||Starting Mode:||Thermal Controlled|
|Zone Management:||Single||Pattern Of Extinguishing:||Enclosed Flooding|
|Agent:||Fm200(hfc-227ea Or Heptafluoropropane)||Spraying Time:||≤8s|
Hanging Automatic Fire Extinguisher Ball Thermally Controlled Server Room
Hanging Fire Extinguisher Thermally Controlled is filled with fm200 agent . It is a kind of colorless and tasteless and non-corrosive and electricity-insulating gas without residue and pollution after extinguishing. It is a friendly-environment gas to be used for extinguishing. Also, because of such feature, it can be used in special place where electrical fire is easy to happen.
The place where the fire is easy to happen, like paint-spraying production line, aging-electrical equipment, rolling machine, printing machine, oil switch, oil immersed transformer, melt impregnating tank, tank, large generators, drying equipment, cement production process of pulverized coal, and the ship's engine room, cargo hold, etc.
It does not need more accessories to consist of system. The extinguishing device can automatically put out fire alone. So the composition of this one is just extinguishing device, just one part. It is one kind of special system or extinguisher.
Here attached below is complete composition of whole system,
Two types of hanging type fm200 fire suppression system have different starting mode.
1. Electromagnetic type:
When a fire happens in the protected zone, a smoke detector can detect the smoke and send signal to the control panel. After receiving the signal, the control panel activates alarm bell to inform people that they should quickly run out from the protected zone if the protected zone is a kind of office, or to tell users that the protected zone has gotten a fire, they should go for a check and refill. After the control panel receiving signal from both smoke and heat detector, it will activate the fire extinguishing system and the fire agent sprays out within 8s.
2. Temperature-based type:
When a fire happens, temperature will slowly climb up. As the temperature reaches to the special temperature of the temperature sensor, the glass ball will be burnt by the high temperature and then fire agent goes out for putting out fire within 8s. Here is a warning for users: we suggest that one protected zone should not have two or above temperature-based fire extinguishers in case that the temperature difference influence the efficiency of the extinguisher.