|Place of Origin:||China|
Payment & Shipping Terms:
|Minimum Order Quantity:||30 set|
|Packaging Details:||Plywood case,Paper carton|
|Delivery Time:||10-15 working days after payment or receipt of L/C|
|Payment Terms:||L/C, T/T, D/P, Western Union，Paypal,Credit Crad,Debit Card|
|Supply Ability:||1000 set per month|
|Zone Management:||Single||Pattern Of Extinguishing:||Enclosed Flooding|
|Standard Of Examination:||GB25972-2010||Color:||Red|
Red 30L Fm200 Fire Extinguisher Auto Temperature Sensor Type
|1||Tank size||8Ltr, 10Ltr, 16Ltr, 20Ltr, 30Ltr|
|4||Maximum working pressure||2.5mpa|
|6||Maximum filling Density||1 kg/L|
|8||Ambient working Temperature||0℃～50℃|
Fm200(hfc-227ea) is a kind of colorless and tasteless and non-corrosive and electricity-insulating gas without residue and pollution after extinguishing. And ODP of it is zero. It is a friendly-environment gas to be used for extinguishing. Also, because of such feature, it can be used in special place where electrical fire is easy to happen.
Through little glass tube and contraction principle, it can be automatic fire extinguisher without any manual manipulation.
Electronic computer room, a data processing center, telecommunications facilities, process control, expensive medical equipment, industrial equipment, library, museum and art gallery, clean room, emergency power facilities, flammable liquid storage area, etc.
The place where the fire is easy to happen, like paint-spraying production line, aging-electrical equipment, rolling machine, printing machine, oil switch, oil immersed transformer, melt impregnating tank, tank, large generators, drying equipment, cement production process of pulverized coal, and the ship's engine room, cargo hold, etc.
When a fire happens, the temperature-sensor hanging type fm200 fire extinguisher :
A fire happens → the temperature climbs high fast → temperature exceeds the specified temperature of the temperature sensing glass ball → the temperature sensing glass ball is burnt by the high temperature → the fm200 fire agent comes out from the cylinder through nozzle for putting out the fire.
1/ When there are some problems, users should call us first and we will send professionals there for repair. Users better should not try to fix it themselves, we are afraid an unprofessional repair will make things much worse.
2/ More than one temperature-based hanging type fm200 fire extinguisher is not suggested in a protected zone. There will be a temperature difference in the room when a fire happens, so if two or more temperature-based type in it, we are afraid that the temperature-based type fm200 fire extinguisher cannot activate at the same time.