Payment & Shipping Terms:
|Actuation:||Electrical Or Manual||Placement:||Hanging On The Wall|
|Type:||Suspension||Pattern Of Extinguishing:||Enclosed Flooding|
|Relief Pressure:||5.0±0.225Mpa||Zone Management:||One Protective Zone|
Multiple Suspension Hfc227ea Systems in One Protective Zone
1. Filling pressure: 1.6Mpa
2. Spraying time: ≤8s
3. Working temperature: 0～50℃
4. Starting mode: Electrical start
1. Clean gas, colorless and tasteless and non-corrosive
2. Electric insulation, utilization for extinguishing of electrical combustion
3. Accurate control of protection zone
4. No need for employment of monitor staff
5. Preparation for storage room
6. Space confirmation of placement for cylinder group
Electronic computer room, a data processing center, telecommunications facilities, process control, expensive medical equipment, industrial equipment, library, museum and art gallery, clean room, anechoic chamber, emergency power facilities, flammable liquid storage area, etc.
The place where the fire is easy to happen, like paint-spraying production line, aging-electrical equipment, rolling machine, printing machine, oil switch, oil immersed transformer, melt impregnating tank, tank, large generators, drying equipment, cement pro duction process of pulverized coal, and the ship's engine room, cargo hold, etc.
It is very efficient for you to protect your possession. Since it is a system, it include extinguishing device to put out fire at short time, specially, shorter than 10 second. It means all agent will be discharged in so short time. Then it will be flooding overall. In addition, it has time-delay mechanism. It is around 2 minute. It means when fire happens, there is enough time left to evacuate people from hazardous place.
Different from piped network type of fm200 automatic fire suppression system, it will be simple to install. Because there is no pipeline installation. If your protective zone is really small and there is no more space to put extinguishing device, this type can be under consideration. Because it will be hanged on the ceiling or attached on the wall.
1. Few devices can be connected together in one room.
2. Ceiling should be fastened and firm