|Place of Origin:||China|
Payment & Shipping Terms:
|Minimum Order Quantity:||1 set of system|
|Packaging Details:||Plywood case or box case|
|Delivery Time:||10-15 working days|
|Payment Terms:||L/C, D/P, T/T, Western Union, Paypal, Credit card|
|Supply Ability:||3000 sets per month|
|Nitrogen Pressure Of Driving Device:||6.0±1.0Mpa(20℃)||Spraying Time:||≤60s|
|Pattern Of Extinguishing:||Enclosed Flooding||Working Pressure:||5.7MPa|
|Cylinder Volume:||70L||Capacity Of Agent:||42kg|
60s CO2 Fire Suppression System,
CNAS CO2 Fire Suppression System
CO2 High Pressure Fire Suppression System
Pressurized CO2 fire suppression system is a kind of intelligent automatic fire extinguishing equipment, which uses pressurized CO2 as extinguishing agent. Pressurized CO2 extinguishing agent won’t cause damage for most things, because of its no residue and non-toxic after extinguishing. This agent still have many advantages: insulating, no water damage and good extinguishing effect.
Depend on different requirements of protection zone, pressurized CO2 fire suppression system can be designed as two kinds of the systems: unit system for single zone; combined distribution system for multiple zones. Adopts enclosed flooding extinguishing to realize the fire protection for single protected zone or multiple protected zones. Our system has three mode of starting: automatic, manual and machine emergency control. The system is advanced technology, high extinguishing efficiency and convenient maintenance.
|3||Filling Volume of Gas||42kg|
|5||Max Working Pressure||12.4MPa|
|7||Max Filling Rate||0.6kg/L|
|9||Working Pressure of Releasing Device||Container Valve: 19±0.95MPa;
|10||Nitrogen Pressure of Driving||6.0±1.0Mpa(20℃)|
|11||Condition of Reserving Room for Container||Temperature: 0~50℃|
Library and archives room, electronic computer room, electrical substation, telecommunication room, hangar, garage, marine engine room, cargo, paint-spraying room, boiler room, control center, etc.
It is suitable for putting out all kinds of the fires of flammable liquid and solid matter; gas fire in which power can be cut off before extinguishing the fire.
Here is the illustration of working principle to whole system,