|Place of Origin:||China|
Payment & Shipping Terms:
|Minimum Order Quantity:||1set system|
|Packaging Details:||Plywood case,Paper carton|
|Delivery Time:||10-15 working days after payment or receipt of L/C|
|Payment Terms:||L/C, T/T, D/P, Western Union,Paypal,Credit Card,Debit Card|
|Supply Ability:||3,00 set per month|
|Volume Of Cabinet:||575L||Capacity Of Cylinder:||120L|
gas fire suppression system,
gas fm 200
Heptafluoropropane Fm200 Fire Extinguishing System For 120L Cabinet
|6||max working pressure||4.2Mpa|
Fm200(htc-227ea) is a kind of colorless and tasteless and non-corrosive and electricity-insulating gas without residue and pollution after extinguishing. And ODP of it is zero. It is a friendly-environment gas to be used for extinguishing. Also, because of such feature, it can be used in special place where electrical fire is easy to happen.
Combined with extinguishing device and electronic accessories, the whole system can be actuated automatically. It can monitor the situation of protective region through detectors and then it can also start the extinguishing device through solenoid actuator automatically. So the whole system can achieve automation totally. Therefore, it can avoid that there is no one who notice the fire when it happens and also it saves much money for employment to supervise the protective area.
Electronic computer room, a data processing center, telecommunications facilities, process control, expensive medical equipment, industrial equipment, library, museum and art gallery, clean room, anechoic chamber, emergency power facilities, flammable liquid storage area, etc.
The place where the fire is easy to happen, like paint-spraying production line, aging-electrical equipment, rolling machine, printing machine, oil switch, oil immersed transformer, melt impregnating tank, tank, large generators, drying equipment, cement pro duction process of pulverized coal, and the ship's engine room, cargo hold, etc.
1. Effective firefighting in relatively small region
2. Simple assembly of device without pipeline ( fire extinguishing device includes: fm200 cylinder, fm200
fire agent, container valve, flexible hose, liquid flow check, nozzle and cabinet.)
3. No extra space to store device
4. Better equipped with electrical elements
1. One cabinet or multiple cabinet type fm200 for one zone
2. Enough space in protective region to place it, such as corner or edge of wall
3. Attention to compare height of cabinet and room
4. The volume of the room should be smaller than 1600 cubic metres and the proportion should be
smaller than 500 square metres.