|Place of Origin:||China|
Payment & Shipping Terms:
|Minimum Order Quantity:||1set system|
|Packaging Details:||Plywood case box case|
|Delivery Time:||10-15 working days|
|Payment Terms:||L/C, D/P, T/T, Western Union, Paypal, Credit card|
|Supply Ability:||300 sets per month|
|Standard Of Examination:||GB25972-2010||Storage Pressure:||4.2Mpa|
|Agent:||Fm200(htc-227ea Or Heptafluoropropane)||Capacity Of Cylinder:||90L|
fm 200 suppression system,
Red Cylinder FM200 Gas Fire Suppression System Easy And Convenient Installation
|2||Scale of Protective region for one zone||area:max single-zone is 800m2 volume:max single-zone is 3600m3|
|6||Nitrogen Pressure of Driving Device||6.0±1.0Mpa(20℃)|
|7||Condition of reserving room for container||temperature: -10~50℃, relative humidity: ≤97%|
|8||max working pressure||5.3Mpa|
|9||min working pressure||4.2Mpa|
Fm200(htc-227ea) is a kind of colorless and tasteless and non-corrosive and electricity-insulating gas without residue and pollution after extinguishing. And ODP of it is zero. It is a friendly-environment gas to be used for extinguishing. Also, because of such feature, it can be used in the special place where electrical fire easily happens.
Combined with extinguishing device and electronic accessories, the whole system can be actuated automatically. It can monitor the situation of protective region through detectors and then it can also start the extinguishing device through solenoid actuator automatically. So the whole system can achieve automation totally. Therefore, it can avoid that there is no one who notices the fire when it happens and it also saves much money for employment to supervise the protective area.
Management of Multiple zones is also in the safe control of the whole system. We can use one system to protect multiple zones through selective valves. It can let the whole system alternative aiming at different protective zone. Agent can be discharged into where the fire happens. It will be very efficient to put out fire in short time. One thing that needs to mention, is that a little room should be prepared to be as storage space for the whole system.
Electronic computer room, a data processing center, telecommunications facilities, process control, expensive medical equipment, industrial equipment, library, museum and art gallery, clean room, anechoic chamber, emergency power facilities, flammable liquid storage area, etc.
The place where the fire easily happens, like paint-spraying production line, aging-electrical equipment, rolling machine, printing machine, oil switch, oil immersed transformer, melt impregnating tank, tank, large generators, drying equipment, cement production process of pulverized coal, and the ship's engine room, cargo hold, etc.
Pipe network fm200 fire suppression device is composed of the following components: fm200 agent, fm200 cylinders, container valves, flexible hoses, liquid flow check valves, a set of manifold, a safety valve, pressure switch, nitrogen driving device(s), driving device frame, gas control pipe, gas flow check valves(it depends), selective valves(it depends), a pair of elbows and flanges, nozzles.
If one set device needs to protect multiple protected zones, its composition is as above. However, if one set system just needs to protected single protected zone, the gas flow check valve and selective valve should be got rid of from its composition.
Every fire suppression system has its strong points. here is going to throw light upon the pipe network type fm200 fire suppression system.
1/ Flexible application in protection zones. As its structure and assembly of other useful components, it can concentrate one very big protection zone with the combination of multiple storage cylinders. Its coverage can be also very small with the system of a single cylinder.
2/ Efficient spraying of gas. One set of pipe network system can make the discharge on average for big zones in a short time with the help of the deployment of the pipeline.
3/ Combined distribution system. The most distinctive and flexible advantage of this system is combined distribution system, which will combine multiple rooms in one district or building but with different dimensions or on different floor. Meanwhile, it can reduce the cost based on the original by the least and safe utilization of fire extinguishing gas. Because of the adoption of selective valves that can guide the fire extinguishing gas into the room on fire, so it would be relatively smarter to monitor each room to avoid an accident. It is worthy to mention that the combined rooms should be at most 8 in accordance with our standard.
Enter Your Message