|Place of Origin:||China|
Payment & Shipping Terms:
|Minimum Order Quantity:||1set system|
|Packaging Details:||Plywood case,Paper carton|
|Delivery Time:||10-15 working days after payment or receipt of L/C|
|Payment Terms:||L/C, T/T, D/P, Western Union,Paypal,Credit Card,Debit Card|
|Supply Ability:||3,00 set per month|
|Cabinet Quantity:||Double||Capacity Of Cylinder:||120L|
|Volume Of Cabinet:||1150L||Pattern Of Extinguishing:||Enclosed Flooding|
|Spraying Time:||≤10s||Max Working Pressure:||4.2Mpa|
Clean Gas Agent HFC227ea Fire Suppression System For Library , Museum
|6||Max working pressure||4.2Mpa|
Fm200(hfc227ea) is a kind of colorless and tasteless and non-corrosive and electricity-insulating gas without residue and pollution after extinguishing. And ODP of it is zero. It is a friendly-environment gas to be used for extinguishing. Also, because of such feature, it can be used in special place where electrical fire is easy to happen.
Combined with extinguishing device and electronic accessories, the whole system can be actuated automatically. It can monitor the situation of protective region through detectors and then it can also start the extinguishing device through solenoid actuator automatically. So the whole system can achieve automation totally. Therefore, it can avoid that there is no one who notice the fire when it happens and also it saves much money for employment to supervise the protective area.
Electronic computer room, a data processing center, telecommunications facilities, process control, expensive medical equipment, industrial equipment, library, museum and art gallery, clean room, anechoic chamber, emergency power facilities, flammable liquid storage area, etc.
The place where the fire is easy to happen, like paint-spraying production line, aging-electrical equipment, rolling machine, printing machine, oil switch, oil immersed transformer, melt impregnating tank, tank, large generators, drying equipment, cement production process of pulverized coal, and the ship's engine room, cargo hold, etc.
Here is the illustration of working principle to whole system,
1. Mechanical parts: cylinder with container valve, cabinet, high pressure hose etc.
2. Electrical parts: smoke detector, heat detector, bell etc.
There must be some suggestion for all the users to have a better use of this system.
1/ The proportion of the protected zone shouldn't be bigger than 500 square metres; the volume should be smaller than 1600 cubic metres.
2/ Users better follow the routine check schedual that we provide them.
3/ If there some problems occur, users better don't fix even touch it themselves. The problems should better know by us and we will send professionals to fix it.
4/ Don't put off the small ball valve's cover unless everything is ready.