|Place of Origin:||China|
Payment & Shipping Terms:
|Minimum Order Quantity:||5 sets|
|Packaging Details:||Plywood case|
|Delivery Time:||10-15 working days after payment or receipt of L/C|
|Payment Terms:||L/C, , D/P, T/T, Western Union, Paypal, Credit card|
|Supply Ability:||200 sets per week|
|Max Working Pressure:||12.1Mpa||Capacity:||42kg Carbon Dioxide|
|Zone Management:||Single||Working Temperature:||0-49℃|
fire detection system,
fire extinguisher tube
Petrochemical Fm200 Fire Detecting Extinguisher 25m 42kg Fire Detection System
|1||Type||Carbon dioxide direct type|
|4||Max working pressure||12.1Mpa|
|6||Density of unit volume||2.5kg/m3|
|7||Max length of detecting tube||25m|
|8||Quantity of agent||42kg|
Indirect Type Of Fire Detecting Extinguisher With Carbon Dioxide is widely used in power plants, communications, broadcasting, petrochemical, railway ans so on system.
Through long detecting tube with gas and pressure inside, it can be an automatic fire extinguisher without any manual manipulation.
It is easiest to be installed and it will save much space after installation. Meanwhile, of course, it will be cheaper without matching electrical accessories or pipe fittings. It is suitable for little cabinet or IT server and so on such device. Because its soft and slender tube can capture subtle ignition inside delicate equipment.
Convenient installation and transportation. Because this system combines fire fighting and alarm function together, and no needs to match electrical elements and pipe fittings, so after fixing the cylinder on a place, all left to do is fixing the detecting tube around a potential source of fire.
This extinguishing device needs no electrical elements and pipe fittings to consist of a system. It can be a fire suppression system itself.
The direct type fire detecting tube fire suppression system is consist of a cylinder, an at most 25m long fire detecting tube, a container valve and two kinds of agents-- co2 and fm200.
The indirect type fire detecting tube fire suppression system has the same components as the direct type except a release tube added. In this system, the fire detecting tube is used for just detecting function, so it needs a release tube together, however, for the direct type, the fire detecting tube can be used for both detecting and releasing.
1 / If there is any problem, please first call and tell us what’s going on and then we will send professionals to help solving the problem. We suggest that users should not touch anything even try to fix it by themselves, because an unprofessional repair may let the problem worse.
2 / There are some routine checks for the system aiming to keep the system in a good condition. Better follow our manual instruction to arrange the frequency of the routine check.
3 / Though it just need fixing on an outer cabinet then can start working, we suggest that users should get everything prepared and then install the system.