|Place of Origin:
Payment & Shipping Terms:
|Minimum Order Quantity:
|Plywood case or box case
|10-15 working days
|L/C, D/P, T/T, Western Union, Paypal, Credit card
|300 sets per month
|Capacity Of Cylinder:
|Automatic Or Manual
HFC227 Gas Fire Suppression System,
FM200 Gas Fire Suppression System
Industrial 70L Model FM200 Gas Suppression System Hfc 227 Gas
|Scale of Protective region for one zone
|area:max single-zone is 800m2 volume:max single-zone is 3600m3
|Nitrogen Pressure of Driving Device
|Condition of reserving room for container
|temperature: -10~50℃, relative humidity: ≤97%
|max working pressure
|min working pressure
One of the agent's strong points, in terms of its description, is that, with the exception of metal fires, it may be applied to all types of class fires. It is also a clean agent. After extinguishing, there is no pollution or residue.
One more is that the FM200 extinguishing system is designed specifically for important devices or assets. It won't cause any harm to your possessions. It is relatively inexpensive and efficient to select it as a fire suppression system.
You can effectively safeguard your belongings by doing this. As a system, it contains an extinguishing mechanism to put out a fire quickly, especially in less than 10 seconds. It implies that all agents will be released thus quickly. There will then be extensive flooding. Additionally, it contains a mechanism for time delay. It takes about two minutes. It means that if a fire breaks out, there will be adequate time to get everyone out of a dangerous situation.
It can allow numerous zones to be safely under one system's management. For large and numerous zones, it will then save a lot of money.
Here is the illustration of working principle to whole system,
The fm200 agent, fm200 cylinders, container valves, flexible hoses, liquid flow check valves, a set of manifold, a safety valve, pressure switch, nitrogen driving device(s), driving device frame, gas control pipe, gas flow check valves (it depends), selective valves (it depends), a pair of elbows and flanges, and nozzles make up the pipe network of the fire suppression system.
If a single set device is required to guard several protected areas, it will be constructed as described above. The gas flow check valve and the selective valve, however, should be removed from the design of one set system if it is only required to safeguard one protected zone.
Below attached is one mimic diagram of 4.2Mpa 70L Model Fm200 Firefighting System