|Place of Origin:||China|
Payment & Shipping Terms:
|Minimum Order Quantity:||1set system|
|Packaging Details:||Plywood case or box case|
|Delivery Time:||10-15 working days|
|Payment Terms:||L/C, D/P, T/T, Western Union, Paypal, Credit card|
|Supply Ability:||300 sets per month|
|Agent:||Heptafluoropropane||Pattern Of Extinguishing:||Enclosed Flooding|
|Actuation:||Automatic Or Manual||Max Working Pressure:||8.0Mpa|
5.6Mpa FM200 Pipe Network System,
Heptafluoropropane FM200 Pipe Network System
Heptafluoropropane 5.6Mpa Fm200 Gas Suppression System With Pipeline
|2||Scale of Protective region for one zone||area:max single-zone is 800m² volume:max single-zone is 3600m³|
|6||Nitrogen Pressure of Driving Device||6.0±1.0Mpa(20℃)|
|7||Condition of reserving room for container||temperature: -10~50℃, relative humidity: ≤97%|
|8||max working pressure||8.0Mpa|
|9||min working pressure||4.6Mpa|
Pipe network fm200 system: multiple management along with selector valve, balanced spraying in big zone through pipeline, management of different layer, overall protection.
Combined distribution system. The most distinctive and flexible advantage of this system is combined distribution system, which will combine multiple rooms in one district or building but with different dimensions or in different floor. Meanwhile, it can reduce the cost based on the original by the least and safe utilization of fire extinguishing gas. Because of the adoption of selective valves that can guide the fire extinguishing gas into the room on fire, so it would be relatively smarter to monitor each room to avoid an accident. It is worthy to mention that the combined rooms should be less than 8 including 8 in accordance with our standard.
1. Choice for storage room, including ambient environment and volume
2. Design of pipeline, including placement of conduits and connection
3. Installation, integration of each parts and connection between parts
4. A separated room needed for storage
Pipe network fm200 fire suppression system is composed by pipe fitting part, fire extinguishing part and electrical element part.
The fire extinguishing part: fm200 agent, fm200 cylinders, container valves, flexible hoses, liquid flow check valves, a set of manifold, a safety valve, pressure switch, nitrogen driving device(s), driving device frame, gas control pipe, gas flow check valves(it depends), selective valves(it depends), a pair of elbows and flanges, nozzles.If one set device needs to protect multiple protected zones, its composition is as above. However, if one set system just needs to protected single protected zone, the gas flow check valve and the selective valve should be got rid of from its composition.
Because of using the whole flooding way to put out the fire, the fire suppression system only fits for those occupied room. Pipe network type fm200 fire suppression system is suitable for those significant several rooms together or a big room. The follow - ups are for reference.
Records and data archives
Electric utility facilities