|Place of Origin:||China|
Payment & Shipping Terms:
|Minimum Order Quantity:||1set system|
|Packaging Details:||Plywood case or box case|
|Delivery Time:||10-15 working days|
|Payment Terms:||L/C, D/P, T/T, Western Union, Paypal, Credit card|
|Supply Ability:||300 sets per month|
|Nitrogen Pressure Of Driving Device:||6.0±1.0Mpa(20℃)||Filling Density:||≤950kg/m3|
|Standard Of Examination:||GB25972-2010||Storage Pressure:||4.2Mpa|
|Agent:||Fm200(htc-227ea Or Heptafluoropropane)||Type:||Piping|
fm 200 suppression system,
4.2 mpa piping gas fm200 system
4.2 Mpa Piping Gas Fm200 Fire Suppression Systems For Telecommunications Facilities
|2||Scale of Protective region for one zone||area:max single-zone is 800m2 volume:max single-zone is 3600m3|
|6||Nitrogen Pressure of Driving Device||6.0±1.0Mpa(20℃)|
|7||Condition of reserving room for container||temperature: -10~50℃, relative humidity: ≤97%|
|8||max working pressure||5.3Mpa|
|9||min working pressure||4.2Mpa|
A type of colorless, tasteless, non-corrosive, electricity-insulating gas that leaves no residue or pollution after being extinguished is known as FM200 (htc-227ea). And it has 0 ODP. It is an environmentally friendly gas that can be used to put out fires. Additionally, this functionality allows it to be used in specific locations where electrical fires are prone to occur.
The entire system can be automatically activated when extinguishing equipment and electrical accessories are used together. It can automatically initiate the extinguishing device using a solenoid actuator after monitoring the situation in the protective area with detectors. So the system as a whole can fully automate. As a result, it may be avoided that no one notices the fire when it breaks out, and it also saves a lot of money on hiring someone to oversee the protective area.
The safe control of the entire system includes the management of many zones. Through the use of selective valves, we may safeguard several zones with a single system. It may enable the system as a whole to aim instead for a different protection zone. Agent can be released into the area of the fire. In a short period of time, the fire will be effectively extinguished. One thing that must be mentioned is that a small room must be ready to serve as the system's storage space.
A clean room, anechoic chamber, emergency power facilities, volatile liquid storage space, a data processing center, telecommunications facilities, process control, pricey medical equipment, a library, a museum, and an art gallery, among other things.
The location where fires are more likely to occur, such as the ship's engine room, cargo hold, rolling mill, printing press, oil switch, oil-immersed transformer, melt impregnating tank, and equipment used to dry large generators and pulverized coal into cement.
1. Mechanical components, such as the driving cylinder with container valve, the frame for the cylinder group, the frame for the driving device, the high pressure hose, etc. Fm200 agent is primarily stored there.
2. Electrical components, such as a bell, heat detector, and smoke detector.
Conduit, connectors, elbows, flanges, and other pipe fittings.
The entire system's composition is attached below.