|Place of Origin:||China|
Payment & Shipping Terms:
|Minimum Order Quantity:||5 sets|
|Packaging Details:||Plywood case|
|Delivery Time:||10-15 working days after payment or receipt of L/C|
|Payment Terms:||L/C, , D/P, T/T, Western Union, Paypal, Credit card|
|Supply Ability:||200 sets per week|
|Max Length Of Detecting Tube:||25m||Capacity:||42kg|
|Actuation:||Automatic||Pattern Of Extinguishing:||Enclosed Flooding|
|Standard Of Examination:||GB25972-2010||Application:||Server Cabinet|
fire detection tubing,
fire detection system
Radio Indirect Co2 Fire Detection Tube 5.7Mpa Working Pressure
|1||Type||Carbon dioxide indirect type|
|4||Max working pressure||12.1Mpa|
|6||Density of unit volume||2.5kg/m3|
|7||Max length of detecting tube||25m|
|8||Quantity of agent||42kg|
Indirect Co2 Fire Detection Tube is filled with 42kg Co2 . This type of extinguishing device can automatically put out fire. When fire burns detecting tube or ambient temperature rises, it will make the tube broken. Then the agent in cylinder will be discharged through pipe.
This kind of system is fit for small spaces , like the power plants , communications , radio , film and television , petrochemical , railway system and so on.
This extinguishing device needs no electrical elements and pipe fittings to consist of a system. It can be a fire suppression system itself.
The direct type fire detecting tube fire suppression system is consist of a cylinder, an at most 25m long fire detecting tube, a container valve and two kinds of agents-- co2 and fm200.
The indirect type fire detecting tube fire suppression system has the same components as the direct type except a release tube added. In this system, the fire detecting tube is used for just detecting function, so it needs a release tube together, however, for the direct type, the fire detecting tube can be used for both detecting and releasing.
The fire detecting tube fire suppression device has the following advantages:
1 / Convenient installation and transportation. Because this system combines fire fighting and alarm function together, and no needs to match electrical elements and pipe fittings, so after fixing the cylinder on a place, all left to do is fixing the detecting tube around a potential source of fire.
2 / Non-electric start mode. It doesn’t need the power to activate the system. This system’s work principle is using its own storage pressure instead of relying on the outside force activating. When the detecting tube is broken by the fire, the agent will discharge.
3 / Little occupation of space. This system is suitable for protecting a system, like telecommunication system, rather than a protected zone. The cylinder fixes on the outer cabinet, and will not occupy many places.