|Place of Origin:||China|
Payment & Shipping Terms:
|Minimum Order Quantity:||30 set|
|Packaging Details:||Plywood case,Paper carton|
|Delivery Time:||10-15 working days after payment or receipt of L/C|
|Payment Terms:||L/C, T/T, D/P, Western Union，Paypal,Credit Crad,Debit Card|
|Supply Ability:||1000 set per month|
|Diameter:||320mm||Capacity Of Agent:||16kg|
|Zone Management:||Single||Pattern Of Extinguishing:||Enclosed Flooding|
auto fire extinguisher,
automatic fire extinguisher ball
Single Zone Firefighting Device FM200 Fire Extinguisher Automatic Or Manual
|4||Starting mode||Temperature start|
Hanging Firefighting Device Of 16l Type is filled with fm200 agent . It is a kind of colorless and tasteless and non-corrosive and electricity-insulating gas without residue and pollution after extinguishing. And ODP of it is zero. It is a friendly-environment gas to be used for extinguishing. Also, because of such feature, it can be used in special place where electrical fire is easy to happen.
Electronic computer room, a data processing center, telecommunications facilities, process control, expensive medical equipment, industrial equipment, emergency power facilities, flammable liquid storage area, etc.
The place where the fire is easy to happen, like paint-spraying production line, aging-electrical equipment, rolling machine, printing machine, oil switch, oil immersed transformer, melt impregnating tank, tank, large generators, drying equipment, cement production process of pulverized coal, and the ship's engine room, cargo hold, etc.
Normally, a complete fire suppression system contains three parts -- fire extinguishing device, pipe fitting and electrical elements. However, the suspense type fm200 fire suppression system does not need any pipe fitting, even the temperature-based suspension fm200 fire extinguisher type doesn’t require electrical elements.
The components of this suspension type fm200 fire suppression are: round cylinder with fm200 fire agent, solenoid actuator ( electromagnetic type ), container valve, pressure switch, nozzle, temperature sensing glass ball ( temperature-based type ).
1 / We suggest that there should be at least a yearly routine check for the whole system. Actually, some components need check weekly, some monthly and the whole system yearly. The frequency of checking better follows the manual instruction we provide.
2 / In our professional considerations, we suggest that one protected room better should not install more than one temperature-based fm200 fire extinguisher. When there is a fire, the temperature of some space near the fire point will go up and some far away point stay cool. Thus this temperature difference is unable to let the fire extinguisher start at the same time, which makes the fire agent cannot ran out within 8s and fails to protect the possession in the room.