|Place of Origin:||China|
Payment & Shipping Terms:
|Minimum Order Quantity:||1set system|
|Packaging Details:||Plywood case box case|
|Delivery Time:||10-15 working days|
|Payment Terms:||L/C, D/P, T/T, Western Union, Paypal, Credit card|
|Supply Ability:||300 sets per month|
|Working Temperature:||-10~50℃||Pattern Of Extinguishing:||Enclosed Flooding|
|Relative Humidity:||≤97%||Storage Pressure:||5.6Mpa|
5.6Mpa FM200 Pipe Network System,
800m² FM200 Pipe Network System
Tasteless Piping Fm200 Fire Suppression System Pipe Network System
|2||Scale of Protective region for one zone||area:max single-zone is 800m² volume:max single-zone is 3600m³|
|6||Nitrogen Pressure of Driving Device||6.0±1.0Mpa(20℃)|
|7||Condition of reserving room for container||temperature: -10~50℃, relative humidity: ≤97%|
|8||max working pressure||8.0Mpa|
|9||min working pressure||4.6Mpa|
1.Clean gas, colorless and tasteless and non-corrosive
2. Electric insulation, utilization for extinguishing of electrical combustion
3. Totally automatic system
4. Accurate control of protection zone
5. Multiple management in the control of the whole system
6. Agent quantity for biggest zone is enough to protect all zones through selector valves
In terms of description of agent, one of its competent advantages is that it can be used for all kinds of class fires except metal fire. And it is clean agent. There is no residue and pollution after extinguishing.
Another one is that fm200 extinguishing system is special for critical assets or device. It will have no damage for your property. Relatively, it is cheap and effective to be chosen as fire suppression system.
It is very efficient for you to protect your possession. Since it is a system, it include extinguishing device to put out fire at short time, specially, shorter than 10 second. It means all agent will be discharged in so short time. Then it will be flooding overall. In addition, it has time-delay mechanism. It is around 2 minute. It means when fire happens, there is enough time left to evacuate people from hazardous place.
It can let multiple zones are protectively in the control of one system. Then it will save much money for big and multiple zones
Below attached is one mimic diagram of 5.6Mpa Piping Fm200 Suppression
1. Mechanical parts: cylinder with container valve, frame for cylinder group, driving cylinder, frame for driving device, high pressure hose etc. It is mainly used for storing fm200 agent
2. Electrical parts: smoke detector, heat detector, bell etc.
3. Pipe fittings: conduit, connector, elbow, flange etc.
The way of putting out the fire: whole flooding way
The process of the system activated: a fire happens → the smoke detector catches smoke and sends signal to control panel → control panel get signal and activates the alarm bell to tell people to get out of the building → the heat detector feels the heat and sends signal back to control panel → control panel gets both signal from smoke and heat detector, after a few seconds' delay, starts the fire extinguishing device → fm200 fire agent sparys from the nozzle and puts out the fire.