|Place of Origin:||China|
Payment & Shipping Terms:
|Minimum Order Quantity:||1set system|
|Packaging Details:||Plywood case or box case|
|Delivery Time:||10-15 working days|
|Payment Terms:||L/C, D/P, T/T, Western Union, Paypal, Credit card|
|Supply Ability:||300 sets per month|
|Nitrogen Pressure Of Driving Device:||6.0±1.0Mpa(20℃)||Spraying Time:||≤10s|
|Standard Of Examination:||GB25972-2010||Pattern Of Extinguishing:||Enclosed Flooding|
|Capacity Of Cylinder:||40L||Type:||Pipe Network|
40L FM200 Gas Suppression System,
800m2 FM200 Gas Suppression System
40L Cylinders Group FM200 Gas Suppression System Pipe Network System
|2||Scale of Protective region for one zone||area:max single-zone is 800m2 volume:max single-zone is 3600m3|
|6||Nitrogen Pressure of Driving Device||6.0±1.0Mpa(20℃)|
|7||Condition of reserving room for container||temperature: -10~50℃, relative humidity: ≤97%|
|8||max working pressure||5.3Mpa||8.0Mpa|
|9||min working pressure||4.2Mpa||4.6Mpa|
Fm200(htc-227ea) is a kind of colorless and tasteless and non-corrosive and electricity-insulating gas without residue and pollution after extinguishing. And ODP of it is zero. It is a friendly-environment gas to be used for extinguishing. Also, because of such feature, it can be used in special place where electrical fire is easy to happen.
Combined with extinguishing device and electronic accessories, the whole system can be actuated automatically. It can monitor the situation of protective region through detectors and then it can also start the extinguishing device through solenoid actuator automatically. So the whole system can achieve automation totally. Therefore, it can avoid that there is no one who notice the fire when it happens and it also saves much money for employment to supervise the protective area.
Management of Multiple zones is also in the safe control of the whole system. We can use one system to protect multiple zones through selective valves. It can let the whole system alternative aiming at different protective zone. Agent can be discharged into where the fire happens. It will be very efficient to put out fire in short time. One thing that need to mention, is that a little room should be prepare to be as storage space for the whole system.
Electronic computer room, a data processing center, telecommunications facilities, process control, expensive medical equipment, industrial equipment, library, museum and art gallery, clean room, emergency power facilities, flammable liquid storage area, etc.
The place where the fire is easy to happen, like paint-spraying production line, aging-electrical equipment, rolling machine, printing machine, oil switch, oil immersed transformer, melt impregnating tank, tank, large generators, drying equipment, cement production process of pulverized coal, and the ship's engine room, cargo hold, etc.
Here is the illustration of working principle to whole system,